Terminal boxes KZG-VEL for heating cables with plane section
Various materialPossibility to install additional indicatorsAvailability of cable gland rack
Permits of the Republic of Kazakhstan
Terminal boxes KZG-VEL are intended for connection and branching of heating cables with plane cross section in AC and DC circuits of electrical units for
chemical, gas, oil and other industries.
The possibility to install clamps for various currents.
The wide range of materials for box manufacturing: plastic, aluminum, construction steel with corrosion-resistant coating or stainless steel.
The possibility to install additional indicators on boxes, for example, for indication of terminal energization.
Boxes consist of enclosure, in which terminal clamp blocks are located, and on side walls explosionproof cable glands are installed. Moreover,
installation of explosionproof LED indicator of IS type is possible.
Cable gland rack is located:
from D side – for boxes KZGP(M)-VEL3.1 and KZGP(M)-VEL3.2,
from C side – for boxes KZGP(M)-VEL2.2.
KZG Х1 – VEL Х2 – ХЗ/Х4 P – РЕ/Х5 – SK – Хn х Хm (Х6) – (IS V Х) –
(DU – Х) – Х7 – V1.5
KZG-VEL – terminal box for wiring of heating cables with explosion protection marking 1ExeIIT5(T4/T3/T2/T1),
Х1 – box material:
SS – stainless steel
S – steel with corrosion-resistant coating
P – plastic (for temperature classes Т5 and Т4)
M – aluminum alloy
Х2 – standard dimension of used enclosure:
Х3 – nominal current of used terminals, A
Х4 – number of clamps for the specified nominal current
P – index indicating use of spring terminals. When installing
terminal screws index is not specified
РЕ/Х5 – index indicated use of grounding terminals and their number. If grounding terminals are not
required, index is not specified
SK – cable gland rack VK-G-VEL located from D side – for boxes KZGP(M)- VEL3.1 and KZGP(M)-VEL3.2 and from С side –
Хn – type of cable gland or plug
Хm – number of cable glands or plugs for each standard size
side for cable gland installation: А, В, С or D (clockwise), moreover, А and С sides – long, В and D – short
(IS V Х) – IS – light indicator. If the indicator is
not required, index is not specified
Terminal box with
explosion protection marking 2ExeIIT5 in enclosure with standard size 3.2 made of plastic, with 6 clamps for nominal current 41A, with three grounding clamps, cable gland rack
VK-G-VELL, additional cable glands: from А side one cable gland with thread М32х1.5 for armored cable from nickel-plated brass, plastic cable gland with thread М25х1.5 and
cable gland from stainless steel with thread М25х1.5 for unarmored cable from С side, yellow light indicator for voltage 220 V, climatic version V and arrangement category 1.5.