|Certificate Type||Product Description||Certificate|
|Permits of the Republic of Kazakhstan||VSU-M|
They are intended for use as stationary light warning means and ensure generation of light signals within explosion hazardous areas according to the explosion protection marking. When installing on high-rise buildings, both obstruction lighting fixtures for light marking and warning lights on high-rise and extended facilities in order to ensure safety for aircrafts, for example, airplanes, helicopters, etc. can be used.
Signal device consists of aluminum body with yellow powder coating. Protective glass is thermal-resistant, extra strong with high light-transmission capability, fixed inside aluminum ring and screwed on lighting fixture.
The body of LED compartment in signal device forms explosionproof enclosure with “d” explosion protection type, and gland compartments has “е” explosion protection. Grounding bolts М5 are installed inside and outside lighting fixture.
Conversion block and terminal clamps are installed inside lighting fixture.
Signal device has 4 entries with thread М25х1.5 that allows laying cable through transit closed with plug on default.
VSU-M – Х1 Х2 – UHL1
Х1 – light-emitting color:
R – red
Х2 – fastening type:
Cl – ceiling
UHL1 is a type of climatic version and arrangement category according to GOST 15150
Example of record for designation of explosionproof signaling device of red light-emitting with ceiling installation, UHL1 climatic version, 1 arrangement category according to GOST 15150:
Explosion protection marking: 1ExdbIICT6, 2ExdеIICT6, Ex tb IIIC T85°C
Level of dust and moisture protection: IP65
Supply voltage: 220 V АС ±10 %, 50 Hz
Power consumption: 40 W
Flashing rate: 16; 20; 30; 40; 60; 80; 120; 240 times per minute
Brightness along axis: 200 cd
Diameter of laid cable: 10–14 mm
Cross-section of connected cores: 3х(1–2.5 mm2)
Class of protection from electric shock according to GOST 12.2.007.0: I
Operation temperature: from -60 °C to +55 °C
Weight, kg: 13.8