Explosionproof lighting fixture for linear fluorescent or LED lamps VELAN51
Availability of reflector increases light efficiency and protect from dust depositionUse of electronic start control gearUse of fluorescent and LED lamps is possible
Permits of the Republic of Kazakhstan
Explosionproof lighting fixtures with the body from Cindal are intended for general lighting of explosion hazardous areas of all classes according to the
explosion protection marking.
Use of electronic start control gear in lighting fixtures VELAN51 allows:
Obtaining service life increase for lamps reducing maintenance expanses.
Excluding lamp blinking when switching on lighting fixture (instaneous starting).
Ensuring high power factor cosφ≥0.98.
There is no need in additional installation of compensator.
Corrosion-resistant materials with special coating ensure long service life.
The possibility to install emergency control block with storage battery ensuring self-contained operation for lighting fixture up to 2 hours (only for lighting fixtures
with 2 lamps (fluorescent and LED)) inside lighting fixture
Lighting fixture consists of aluminum body of cylindrical form with powder coating. Light transmitting element is made of shockproof borosilicate glass.
Circuit engineering of lighting fixture with lamp and electronic start control gear are located in the body with “explosionproof enclosure” type of explosion protection. When
ordering lighting fixture with storage battery storage battery and control block shall be additionally installed. Installation of two cable glands for transit laying of power
cable. Lighting fixture grounding is ensured by internal and external grounding bolts.
AK – index indicating availability of storage battery in the lighting fixture and the possibility of lighting fixture operation from it. If storage battery is not required, index shall not be specified The storage battery is installed only on the lighting fixtures with 2 lamps (fluorescent and LED)
SD.L. – index indicating use of LED lamps (only for SD.L.9 and 18).
For linear fluorescent lamps, index is not indicated.
Х1 – number of lamps in lighting fixture: 1 or 2
Х2 – power of lamp used in lighting fixture:
fluorescent – 18 W, 36 W or 58 W
linear LED lamp – 9 (replacement of fluorescent lamps 18 W); – 18 (replacement of fluorescent lamp 36 W)
Х3 – fastening type:
Cl – ceiling
P – on pole
Х4 – explosion protection marking: 1ExdIICT6
X5 – type of climatic version and arrangement category for lighting fixture according to GOST 15150:
U1 – for lighting fixtures with fluorescent lamps
UHL1 – for lighting fixtures with LED lamps
Example of designation record of lighting fixture for two linear fluorescent lamps having power 58 W, ceiling mounting, climatic version and arrangement category U1:
“Lighting Fixture VELAN 51-2х58P-1ExdIICT6-U1”
Example of designation record of lighting fixture with storage battery for two linear LED lamps having power 18 W, ceiling mounting, climatic version and arrangement category UHL1: