Explosionproof junction box for lighting equipment VAD-RSP
4 typesManufacturing from aluminum alloy or cast iron depending on box typeReliability, strength, convenience of cable connection
Permits of the Republic of Kazakhstan
FIRE SAFETY CERTIFICATE
Used as junction box and/or fastening element for lighting equipment installed within explosion hazardous areas. In boxes with hole there is a possibility
to arrange inside video camera, microwave motion sensor, light sensor or other equipment.
Box structure is convenient for transit cable laying.
Small overall dimensions and weight.
The possibility to manufacture with hole.
The body is made of aluminum alloy or cast iron with powder coating.
The box has two types of body:
round body has 4 thread entries for cable glands;
VAD-RSP-F, G: from round body three branch pipes with female thread are laid. Two
branch pipes are displaced from the center to the strip side for box fastening on plane surface to ease transit cable laying. The third branch pipe has stop screw used to
prevent torque failure of connected pipe or reducing coupling.
Inside the body terminal clamps are installed.
Grounding bolts are installed inside and outside
The box cover is screwed into the body by thread.
Protective light transmitting element is made of polycarbonate, extra strong, with high light
transmitting capability integrated into the cover.
Boxes F and G are used as main parts for fastening of lighting fixtures.
VAD-RSP – Х0 – Х1/Х2 – UHL1
VAD-RSP – explosionproof junction box
Х0 – availability of inspection hole “О”
Х1 – type of junction box: D, F, G. Mode details about
types and distinctions of boxes can be studied from the Table
Х2 – cable glands and number or type of thread
UHL1 – type of climatic version for
condulet according to GOST 15150.