Explosionproof cable glands for armored and unarmored cable, pipe laying VK-VEL
Wide range of diameters for sealed cables: from 5 mm to 112 mmMaterial: steel with coating, stainless steel, brass with coatingDesign reliability and simple structure
Permits of the Republic of Kazakhstan
Maritime Register of Shipping
Fire Safety Certificate
Cable glands are intended for glanding and fixing flexible armored and unarmored cables with rubber and plastic insulation with A round section when
laying into stationary, mobile or portable electrical
Cable glands with ExeIU/ExeIIU and ExeIIU explosion protection marking according to GOST 30852 are Ех-components and are intended for use in explosion protected electrical equipment of groups and II with explosion protection level – “increased reliability against explosion” according to GOST 30852. Cable glands with ExdIU/ExdIIСU and ExdIICU explosion protection marking according to GOST 30852 are Ех-components and are intended for use in explosion protected electrical equipment of groups I and II with explosion protection type – “explosionproof enclosure (d)” according to GOST 30852.
Pipe cable glands are made with female pipe thread, can be delivered with male pipe thread at outlet by special order.
There is a wide range of entered cable for both armored and unarmored cable.
Cable glands for unarmored cable consist of a fitting installed in equipment, a seal ring, which ensures cable glanding, a cap nut, which puts
pressure on the seal ring through a reducing bushing. Two strips with screws are installed on the cap nut of the cable glands with index 1 and 2 for additional cable fixing
In addition to the aforementioned for armored cable, the glands have rings and bushings with a taper surface, between which cable armor is fixed. In cable glands intended for connection of pipe or coupling of MMRn type at the cap nut end, there is an entry with the appropriate thread. Cable glands with index 1BM and 2BM have an additional seal ring to ensure IP with an additional cap nut.
VK – Х1 – VEL Х2 Х3 – Х4 – Х5 – Х6 – V1.5
VK – cable gland
Х1 – cable gland material:
Br – brass
SS – stainless steel
S – steel with corrosion-resistant coating
VEL – “VEL” series
Х2 – figure
indicating gland version:
1 – for glands with ExeIU/ExeIIU or ExeIIU explosion protection marking (for pipe gland)
for glands with ExdIU/ExdIICU or ExaIIU/ExdnCu or ExdIICU explosion protection marking (for pipe gland)
3 – for glands with ExeIIU explosion
4 – for glands with ExеIIU/ExdIICU explosion protection marking
Х3 – index:
B – for
glands intended for armored cable gland
M – for upgraded glands with a device for prevention of cable armor tears