Box universalityMounting easeIncreased strength when keeping small weight
Condulets KPххS made of sheet steel are intended for connection and branching of flexible or armored cables with elastic or thermoplastic jacket of round
and plane cross section with copper or aluminum cores in AC and DC circuits of electrical installations of chemical, gas, oil and other industries.
Special coating (melamine-alkyd enamel) being resistant to environment aggressive action, for example, periodic actions of mineral oils, gasoline and water is intended for
operation outdoor within areas with cold and temperate climate.
Upon agreement with the customer completing with any number of glands and combinations of Ех-components, clamps, terminal blocks and cable glands of other manufacturers
having conformity certificates for explosionproofness is possible.
The box consists of the body and cover made by method of deep drawing from steel sheet. Installation of cable glands is possible from each side of the
box. The box is equipped with four grounding bolts located outside and two grounding pins located inside the box.
X3 – number of cable glands (at number over 9 glands figures designating number of cable glands shall be specified in brackets)
condulet side or alphabetic code for arrangement of glands according to work order agreed with the manufacturer
Х4 – nominal voltage: 220 V, 380 V or 660 V
Х5 – type of climatic version and arrangement category according to GOST 15150: U1, HL1, OM1, T1
Х6 – explosion protection marking: 1Ex e IIC T5 Gb/Ex tb
IIIC T95°C Db
Not indicated for condulets with explosion protection marking 2ExeIIT5
Example of order forming:
That corresponds to:
Condulet for nominal voltage 380 V, mains frequency 50 Hz for 24 terminal clamps, with two cable
glands 1-(Ø12 mm) with “D” arrangement, with two cable glands 2-(Ø25 mm) with “E, H” arrangement, with one cable gland 3-(Ø30 mm) with “L” arrangement, two cable glands 4-(Ø40
mm) with “B, G” arrangement, climatic version and arrangement category U1
By special order condulets are made with pipe glands of VK series and with
metal cable glands of VK-VEL series (s/o).
Cable glands are not installed in boxes KP48PS and KP64PS from “B, G” sides.